Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
the flame detector rod is dirty? try cleaning with sand paper and scraping also. there should be a small amp. reading threw wire coming from flame detector rod. in milli amp range. increases when running. some times i use a jumper to hold gas valve on once started to allow time to test amps.
Posted on Feb 21, 2008
Remove all power from the furnace, it is likely the brain in the furnace is need of being reset, from the battery replacement, why did you change the battery, was there an indicator telling you to change it?
Many times just removing all the power to the furnace will do the trick with a reset, if not let me know and we will go from there, but it sounds like the main brain is confused or bad, more likely confused, so try the power removed first.
Than let me know firstname.lastname@example.org
Posted on Nov 22, 2008
having a problem with a weather maker 8000. It will not come on at all unless I shut down the switch on the side of the furnace. filters is clean. it will start to light then stop
Posted on Dec 20, 2008
Make sure a back draft in the flue is not happening. Wind can blow it out until the flue heats up. The flame sensor may not be close enough to the burner flame. It may be weak and need to be replaced or if its an optical one it may be dirty and not see the flame very well. Its not wasting much gas but it puts extra wear and tear on the gas controls, is noisy, and, as you said, blows cold drafty air. A gas control system that has issues of any kind is not real safe. It needs to get fixed.
Posted on Jan 08, 2009
Tips for a great answer:
Oct 12, 2013 | Heating & Cooling
Oct 10, 2012 | Amana GMVC80905CX Gas Furnace
Nov 05, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Feb 11, 2011 | Heating & Cooling
Mar 25, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 08, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 17, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 03, 2007 | Carrier XHB123D X/Y Series Heat/Cool Air...
94 people viewed this question
Usually answered in minutes!