Question about Ruud Matching Split Air Conditioner
Working fine. I cut it off and opened windows over night. Next day I cut it back on and it doesn't cool It seems to run fine but doesn't cool.I think compressor is not running.Any help would be greatly appreciated. Thanks
Hi, Is the condenser fan running? If not, Check the circuit breaker inside the house and the quick disconnect at the condensing unit. Making sure the power is off, check for any bugs in the contactor. If it is running, check to see if there are any resets on a high pressure switch or control board in the condenser. Check the compressor capacitors and see if they are leaking oil or swelled up. are there any burned wires? Is the compressor hot? If the fan is running and the compressor is not hot it is probably off on Low Pressure and needs charged by a licensed Air Cond Tech. Hope I have helped. Let me know. kstfas
Posted on Sep 25, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 19, 2017 | LG Heating & Cooling
Aug 08, 2011 | 1994 Volkswagen Golf
Apr 27, 2011 | Intermatic T104 24h 208-277v Mechanical...
Dec 05, 2010 | Heating & Cooling
Jun 09, 2010 | Kenmore 55612 / 55614 / 5561 / 655619 Side...
Mar 21, 2010 | Ruud Heating & Cooling
Dec 06, 2009 | Ruud UAMB042 Air Conditioner
Jul 30, 2009 | GE (PSS26MSRSS) Side by Side Refrigerator
Jun 15, 2009 | Heating & Cooling
Jul 22, 2008 | Heating & Cooling
182 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: