Question about Heating & Cooling
Capacitor of blower motor need to be check of it ok you need a new motor
Posted on Nov 12, 2013
Pls send me snap of your furnace controller , i can help you
Posted on Oct 15, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Remove all power from the furnace, it is likely the brain in the furnace is need of being reset, from the battery replacement, why did you change the battery, was there an indicator telling you to change it?
Many times just removing all the power to the furnace will do the trick with a reset, if not let me know and we will go from there, but it sounds like the main brain is confused or bad, more likely confused, so try the power removed first.
Than let me know firstname.lastname@example.org
Posted on Nov 22, 2008
I have serviced these furnaces for 20 years and I can tell you most of these models did not have diagnostic lite on them. (although some did, especially if the control board has been replaced) The problem is most likely a bad 3 wire pilot. This will cause exactly what you describe. 2 things to consider though. 1, If you were to replace the pilot don't get a cheaper knockoff. In my experience these do not last long at all. Get the right one from a carrier dealer. It will cost more but be much more reliable. 2 What is the condition of the secondary heat exchanger? Most if not all of the sx series had issues with the secondary heat exchangers rotting out and leaking. If the furnace is out of warranty you would be much better replacing the furnace as the cost of replacing the secondary heat exchanger will probably be almost the same as a new furnace. ( those babies are EXPENSIVE!)
Posted on May 01, 2010
Tips for a great answer:
Jun 06, 2016 | Carrier Weathermaker 8000 Gas Furnace 125k...
Sep 19, 2017 | Carrier Weathermaker 8000 Gas Furnace 125k...
Nov 08, 2011 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 04, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Oct 14, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 30, 2008 | Heating & Cooling
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 17, 2007 | Heating & Cooling
268 people viewed this question
Usually answered in minutes!