Question about Heating & Cooling
Have u got it set to heating and hot water.....Also check ur circulating pump is working
Posted on Oct 12, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
There are 2 Heat Exchangers and 2 Water Pumps on a Combi, at least the one I had when I lived in the UK did.
There is a Thermal Cut Out on both. They look like a Disc, that is Soldered [with provision for connecting the wiring] onto the Hot Water Outlet from the Exchanger to the Pump, to Supply either the Domestic Hot Water, or on the other Exchanger, Central Heating.
If 1 of these fails, the System will start up and when the temp reaches a certain point will trip out the Burner, and continue to Run the Pump until the Temperature drops, and then Stop.
The type I had, had Pumps with a Black front facind nut, this unscrews anti clockwise to release that center, that could be pulled slightly, and used as a Key to turn the Pump Impeller, in the event that lack of use would make it stick, when powered up.
There shouId be a Diagram, inside of the Front Panel, that shows the layout for the whole Internal Water flow, Pipes, Pumps, Safety devices etc. I hope this has helped you.
Posted on Aug 30, 2009
balance the rads.
upstair radiators turn all valves off,heat will then divert downstairs,open valves upstairs 4 turns on locksheilds and number 4 on trvs if u have any.
then if that does not work get a combi or powerflush.
if u cant afford then drain a little from rads,get x300 sludge remover from plumb shop and put in header tank(not hot water tank).
then fill system up and repeat balancing.
Posted on Jan 24, 2010
Tips for a great answer:
Apr 30, 2017 | Water Heaters
Oct 27, 2009 | Protech Systems FasNSeal FSWMKE4 4" Vent...
Oct 19, 2009 | RTO Ariston Gl4.0 Instantaneous Electronic...
Apr 14, 2009 | Emerson Water Heaters
Feb 19, 2009 | Combi Centre DX - Mango
Dec 28, 2008 | Kitchen Appliances - Others
Nov 02, 2008 | Combi Centre DX - Mango
Jun 06, 2008 | Heating & Cooling
Sep 21, 2017 | NewAir Heating & Cooling
26 people viewed this question
Usually answered in minutes!