Blower motor will not come on. i have a rheem furnance
Turn your fan from auto to on at thermostat, if fan doesnt come on.
Remove blower motor door to get to control panel-Turn poweroff !
Try to turn blower wheel to see if it will turn freely,
Remove thermostat wires from control board, put a jumper wire between
r and g.Put door back on and restore power, fan should run. If it does
than it is possible you have a burnt out speed on whatever cylcle heat/cool you are trying to use.
To troubleshoot this-turn power off and find where the blower wires go to
control board. exchange the wires from park to heat or cool terminals.
put cover back on and restore power.IT should work,if nothing happens then you probably have a problem with blower
Feb 13, 2010 |
Heating & Cooling