Question about Williams Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: How to reset vent safety switch
the reset is at the top left side of the furnace. take the cover off n press the red button. the switch could be failing but CHECK drafting through the furnace. hold a flame at the top of the furnace n make sure its pulling inward. u could have a blocked vent pipe or vent cap which will cause excessive heat n tip the safety switch. good luck!
Posted on Nov 24, 2009
Assuming the pilot is clean and sharp. Before replacing the valve, clean any spade connections, those going up to the spill switch in particular. Clean and tighten all 4 connections. Good luck.
Posted on Jan 11, 2010
The problem is with the thermocouple.... this is the metal thing that the pilot flame hits when it is burning....if the flame is not hitting it then it does not get hot enough...
make sure the flame is hitting it....if not then adjust the hood over the flame to get it on the thermocouple...
If it is hitting it then replace the thermocouple....for that heater though the thermo is probably and OEM part and may have to be bought from the manufacturer...
Posted on Nov 07, 2010
The thermocouple is bad and needs to be replaced...
The thermocouple is the copper rod that sticks up into the pilot flame and then screws into the gas valve...
they are sold by lentgh so you need to measure the old one when you go to buy a replacement...
Posted on Jan 06, 2011
Tips for a great answer:
Oct 30, 2017 | Williams Heating & Cooling
Dec 01, 2016 | Williams Heating & Cooling
Dec 08, 2015 | Williams Heating & Cooling
Nov 08, 2013 | Thermos 3509622 Heater
Feb 19, 2013 | Williams 14,000 Btu/hr Direct-Vent Furnace...
Jun 19, 2011 | Williams 3003622 Ceramic Wall Mounted...
Feb 26, 2011 | Williams 3003622 Ceramic Wall Mounted...
Nov 11, 2010 | Williams 6508732 Gas Heater
Dec 09, 2009 | Williams Heating & Cooling
Aug 31, 2017 | Heating & Cooling
39 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: