Question about Goodman Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: GKS91155DXAD Not finishing cycle
Check the heat anticipator setting on the thermostat if its a mercury type thermostat. It may not match the proper amp draw. Take the cover off and it is a little metal lever. Try different adjustments to see which are better. If its a digital thermostat it may have an internal setting. There are several other possible reasons this could happen but that would be the most likely. for more infor on self diagnosis or the like check out my fave website Ra-Jac Air Conditioners and Heaters TX for repair information.
PS: If its a new installation it should have a one year warantee so call back the person who put it in. If you did it yourself be extremely careful gas furnaces can be dangerous. You might want a service person to check the job out for safety hazards. Good Luck with it.
Posted on Feb 29, 2008
If the burners do not fully ignite, the sensor will shut the furnace down. The lack of sufficient burner flame is a gas valve or gas pressure problem within the valve.
Replacing the gas valve with the original one may get you going. I surely suggest a professional service company for safety reasons and a thorough inspection. A 20 year old furnace is past it's normal life span.
Posted on Jan 06, 2009
Cleaning the flame sensor has nothing to do with blower motor not turning on. You either one of the following problems 1 bad cap for motor. 2 bad motor. 3 bad limit on blower housing or 4 a bad board. You will need a volt meter to check for these problems. Try seeing if the fans runs with unit of and fan switch turned to on. Also does motor hummmm. Is motor cage free ( can check by manually turning) If motor doesnt humm and the cage is free wheeling then you will need to find out if you have power going to the motor. If you find out that you do then you will need to change blower motor. If you do not have power then you will need to check limit with continuity tester on volt meter. If that checks fine only 1 thing can be wrong and that is the board.
Posted on Feb 16, 2009
Between the burners is a small rail in the pressed steel where the flame runs across to light the other burners and it sounds like there is dirt or debris in the step over rails causing the problem. You will need to use some compressed air on those rails to clear them out. Once the rails are clear the other two burners should ignite right away.
Posted on Dec 21, 2009
Testimonial: "I did not expect such a quick response. These are hard times for us and we really appreciate your help. Thankyou for sharing your expertise."
Tips for a great answer:
Jan 06, 2015 | Goodman Heating & Cooling
Oct 22, 2013 | Goodman GMS90703BXA Heater
Nov 29, 2012 | Watches
Jan 08, 2010 | Goodman Heating & Cooling
Dec 17, 2009 | Goodman Heating & Cooling
Nov 04, 2009 | Goodman GDS80904BNA Open Flame Heater
Oct 28, 2009 | Goodman GDS80904BNA Open Flame Heater
Oct 19, 2009 | Goodman GMS90703BXA Heater
Oct 11, 2009 | Goodman GDS80904BNA Open Flame Heater
Feb 08, 2009 | Goodman GDS80904BNA Open Flame Heater
249 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: