Question about Coleman Heating & Cooling
Alot of water collects in the pan when using my central air, sometines it over flows and wets the floor.
My first reaction is that it sounds like a plugged or partially plugged drain line. Clear the drain line by either blowing through it backwards (carefully) or using compressed air. In a worse case the line could be kinked or rotted. Make sure the drain can run freely into its destination. Sometimes the line will need to be disassembled to clean it.
Another cause of this can be static pressure imbalance on the fan...the drain trap should be equal to or just less than in height of the total static pressure of the fan in inches of water column so the water (condensate) is not held back by the fan pressure. Make sure your filter is clean, especially if you have pets.
Posted on Apr 21, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 03, 2017 | Cars & Trucks
Jul 22, 2013 | Royal Sovereign White 1200 BTU/12,500...
Jul 31, 2011 | Heating & Cooling
Jul 08, 2010 | Frigidaire FRT18KB2CW Top Freezer...
Apr 22, 2010 | Kenmore 54701 Dehumidifier
Nov 07, 2009 | Amana SXD524VW Side by Side Refrigerator
Jan 06, 2009 | GE (PSS26MSRSS) Side by Side Refrigerator
Jul 14, 2008 | Sunbeam Heating & Cooling
85 people viewed this question
Usually answered in minutes!