Question about Goodman CLQ36AR49 Air Conditioner
I'm assuuming you are talking about your furnace or 2nd. stage heat, when you say piggyback system. Yes you can go to your thermostat or furnace and disconnect just the 2nd. stage heat wire(see furnace wiring diagram), this will not allow the heat to come on in the furnace but it will still allow the indoor blower to run and the heat pump.
Posted on Apr 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 05, 2016 | Heating & Cooling
Jan 17, 2016 | Toys
Feb 27, 2015 | Carrier 52CQ-312-4 Comfort Series Heat...
Oct 15, 2014 | John Deere 420,1020,2010,2020,2510,2520...
Jan 26, 2014 | Heating & Cooling
Jul 01, 2017 | Honeywell Programmable Thermostat Heater
Dec 16, 2009 | Plumbing
Mar 10, 2009 | Hyundai Motor 2003 Elantra
Jan 23, 2009 | GE Zoneline AZ55H09D Air Conditioner
168 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: