Question about Heating & Cooling
I have a bryant ac that is freezing up.The filters are clean the evap is clean. It does not freeze consistently. Also it was pouring water over about 1 month ago. that has stopped and it is discharging outside. It is 110 during the day and about 90 at the ev ening. This happens every year- we have had it serviced and they find nothing wrong- any ideas
Make sure the condensate drain is clean and clear of any debris. With the indoor unit off, Remove the inspection panel and pour a gallon mixture of 10% Bleach to Water solution in the drain pan. Do not overflow the pan but check to make sure there is flow to the outside or drain. Clean out the drain hose if you have to. A freezing coil is a sign of either not enough air going across it or not enough charge in the system. Check to make sure all of the return air vents as well as supply vents are in full open and unrestricted. If they are, you will need to have the charge checked. If this turns out good, have your technician install an anti-freeze kit. This kit will temporarly turn off the compressor unit for a short period when the sensor in the kit experiences a freezing condition. Then after a bit, it will turn on the compressor. It may not cool as much as it was, but it may get you thru. Good Luck!
Posted on Sep 14, 2007
Have an HVAC tech recover the refrigerant from the unit an recyle it during the recovery. Remove any old filter dryers installed on the unit and replace with a new one! YES! Braze in new ones! Pull a triple vacume on this sytem down to 500 microns to insure all non-condensables are evacuated from the system. Weight the charge of refrigerant back in and set by superheat readings from the evaporator coil to the compressor! majic number is 40f evap outlet plus 12f to make it around 52-55 at the compressor inlet. Your problem has been restrictions in the refrigeration cycle either in capillary tube with orfice for metering device or a TXV getting cloged with ****! Hope this gets it solved for you!
Posted on Aug 22, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 20, 2014 | Goodman Heating & Cooling
Jun 30, 2017 | Haier Amana Apn14ke-E 14 000 Btu Portable...
Jul 24, 2012 | Heating & Cooling
Jul 12, 2012 | Carrier Heating & Cooling
Sep 08, 2011 | Heating & Cooling
May 26, 2011 | LG Heat cool Window Air Conditioner
Jun 05, 2010 | Dometic Rooftop RV Air Conditioner
Jun 19, 2009 | Whirlwind FH-778 Air Conditioner
2,150 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: