Question about Humidifiers
I have installed a Honeywell HE265DG115 by-pass humidifier that has a digital control and a remote outdoor sensor. It is wired per the Honeywell Owner's guide, and it does not work. I have had my heater svc. tech, and his friend who is a HVAC contractor try to get it to work. None of us have been successful. My thermostat is new, a Honeywell TH6000, and it is wired back to a Thermo Pride warm air heater with A.C.
I have a wiring diagram that is in .jpg format that is a better illustration than trying to discribe it in less than 1000 words. I tried to attach it to this box but was unsuccessful.
I would appreciate any assistance any can offer. Thank You
The soliniod requires 24v to open so if you dont have the power then its not wire properly. Are you using a current sensing relay to allow the humidifier to only come on whe the fan is operatin? if you do have 24v on solinoid and its not opening then you got a bad solinoid. sometimes the humidistat will be a universal, for a power humidifier . A bypass requires external power and the humidistat will need to be switched to BYPASS to regonize this
Posted on Sep 13, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 20, 2013 | Honeywell HM512DG115 TrueSTEAM 12-gallon...
Try white vinegar instead. The same type of scale builds
up in drip coffee makers. Most recommend white vinegar to remove the scale that
builds up over time. The added bonus is it costs less and is completely safe. If your unit is a water over paper media humidifier, you would be much easier to replace the paper media.
Sep 12, 2012 | Honeywell HM509DG115 120V TrueSTEAM...
Dec 08, 2010 | Honeywell Humidifiers
Sep 14, 2010 | Honeywell Humidifiers
Nov 18, 2009 | Honeywell HE360A1027 Whole House...
Jan 31, 2009 | Honeywell HE360A1027 Whole House...
Jan 09, 2009 | Honeywell Power Humidifier: Furnace...
Dec 25, 2007 | Honeywell HE120 Humidifier
437 people viewed this question
Usually answered in minutes!