Question about Heating & Cooling
Compressor and large line from top of compressor freezing.
Hello do you have a Soleus KFR-18w/d mini/split
If so I have the same problem
Posted on Jan 26, 2008
THE LAST THING TO SUSPECT IS "LOW ON REFRIGERANT". MAIN CAUSES IN ORDER: "OVERCHARGED",DIRTY FILTER, DIRTY COIL, BLOWER MOTOR IS HEATING-UP AND SHUTTING OFF ON INTERNAL OVERLOAD PROTECTOR, ANY THING THAT MAY BE RESTRICTING AIR FLOW IN THE AIR HANDLER, NON-CONDESEBALES, LOW REFRIGERANT. I FIND ON MOST LOW CHARGED UNIT THE "SUCTION" LINE IS WARM AND THE EVAPORATOR COIL IS FROSTED. YOU ONLY GET ICE BACK ON THAT LINE ON THE COMPRESSOR IF YOU VISUALLY LOOK AT THE EVAPORATOR COIL. A COIL THAT IS ICED UP IS LACK OF AIR OR A OVERCHARGE. A LOW SECTION OF SOLID ICE INDICATES A LOW CHARGE.
Posted on Sep 27, 2007
If the top of the compressor is freezing you either have low refrigerant or a restriction in the coil. Check the air filter and change if necessary. Turn the outside unit off using the outside disconnect found a few feet away from the condenser. Let the indoor unit blow air for a few hours to melt the ice off of the coil. Turn back on the outside unit and after about a half hour, you should feel the cool air from your ducts. If the cool air gets warmer over the next hour, you will need a tech to look for leaks and recharge your unit. If it continues to blow warm air even after the 3-hour wait, you have other issues. To answer your original question, on the indoor unit you will find access panels that can be removed for inspection and cleaning. They are commonly located where a 3/4" drain pipe exits the cabinet. While the unit is off, remove these panels and inspect for a buildup of debris. Good Luck!
Posted on Sep 12, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 02, 2013 | Ruud Heating & Cooling
Aug 30, 2011 | Ruud Heating & Cooling
Dec 13, 2010 | Ruud UAMB Air Conditioner
Jul 18, 2010 | Ruud UBHC Air Conditioner
Feb 01, 2010 | Ruud UAMB Air Conditioner
Jan 21, 2010 | Ruud Heating & Cooling
Jan 10, 2010 | Ruud Handle Air Conditioner
Nov 12, 2008 | Heating & Cooling
Apr 10, 2007 | Ruud UBHC Air Conditioner
590 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: