Question about LG Art Cool LA121CNP wall/window Air Conditioner
Getting codes 33 an 44 when i restart the system outside from the breaker it make a few strange sounds. inside units give codes 33 and 44 from cool art and the other blinks 3 times on each led
I may not be of much help but I may be able to guide you into some diagnosos. If there is a communication problem between the inside and outside unit, both on the inside and outside units a colored LED will bling 5 times then pause for 3 seconds. The 33 and 44 codes are confusing to me because I have never seen this. Try resetting the outside unit with no call for heat or cool from the inside unit. After about 20 seconds, restore power to the outside unit. Go in and turn on the remote and make sure you lower the cool setting more than degrees cooler than the room temp. After 3 minutes the outside unit should turn on. If you get an error code of either 1, 2 or 5 blinks document it for the technician. If you continue to get your 33 and 44, you have a bad control board. If all else fails, press and hold the button located on the lower left side of the art unit and hold for about 5 seconds. If it still no longer works, now you will need the help of someone who knows these units.
Posted on Sep 09, 2007
Error code 33
Posted on Jan 15, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Apr 07, 2017 | Mitsubishi Heating & Cooling
Jul 02, 2015 | Senville 24000 BTU Energy Star Ductless...
Jun 04, 2015 | Carrier Heating & Cooling
Sep 12, 2014 | Fujitsu Heating & Cooling
May 26, 2014 | LG LSU307HV 30,000 BTU Ductless SingZone...
Nov 20, 2017 | LG LSN091HSV Super High Efficiency...
May 14, 2010 | LG LA185HV Split System Air Conditioner
May 02, 2010 | LG LA185HV Split System Air Conditioner
Dec 05, 2008 | GE Quiet-Aire Ductless Split System Air...
Jun 23, 2014 | LG Art Cool LA121CNP wall/window Air...
665 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: