Question about LG LS-L1210CL Mini Split Air Conditioner
When I open my LG, the fan in the outside part of my AC doesn't run. The inside part provides some air for few minutes and then my breaker overloaded and turned off. Is is the fan on the outside part that is the problem???....What can I do to resolved it?
If it is the compressor at fault it will be at the discretion of the manufacturer as to what they replace. I would suggest you contact an aircon engineer who can help you diagnose the problem because a professional will have to be in touch with the manufacturer. As you are getting in touch with the contractor who supplied the equipment that will be the correct route to go. Hope this helps.
Posted on Sep 09, 2007
On most air cons there is a time delay before the outside unit starts and LG are no exception. This function means that erratic power supplies wont kill the compressor (outside bit). If the internal fan runs for a few minutes and then the trip goes then it sounds like you have a faulty compressor. This tends to be a scenario for a failed compresssor. What you can try is putting the unit on FAN ONLY (no cooling) and see if the power stays on. If you are more technically competent you could isolate the power to the compressor on the external unit (AFTER ISOLATING THE POWER TO THE WHOLE SYSTEM). And then try putting it on cooling to see if the external fan works. If the trip is not thrown then you have a faulty compressor. I would also like to point out that most A/C manufacturers offer a three year parts warranty so you may have some sort of cover depending on the age of your unit. In which case get an aircon guy out who knows what they are doing (personal reccomendation is always a good starting point). Hope this helps.
Posted on Sep 07, 2007
Tips for a great answer:
Aug 15, 2016 | LG Electronic Window Air Conditioner
Nov 25, 2013 | LG LAN186HV / LAU186HV 18,000 BTU 15 SEER...
Sep 07, 2011 | Air Conditioners
Aug 08, 2011 | Carrier 38CKC042 Air Conditioner
Aug 30, 2010 | Air Conditioners
Dec 29, 2009 | LG Air Conditioners
Aug 15, 2009 | Air Conditioners
Jul 20, 2009 | Air Conditioners
Aug 26, 2007 | Ruud UAKA037 Air Conditioner
198 people viewed this question
Usually answered in minutes!