Question about Fahrenheat FFH1615 Heater
I need to install a used fan forced room heater. I don't know the correct wiring sequence to my power source. It is a 240/208 volt. It has two loose black wires, one from the temp control and one from the fan motor. also, a green wire that connects to the fan motor. No loose white wires visable.
You can be assured that the element is 240 volt. The fan motor is also rated at 240 volt. the wires you have black - black are the connections you make to the line. Use a 12/2 with ground. Use a double pole 20 breaker in your panelbox. The green wire is the equipment ground - connect this to the bare wire from the 12/2. On the 12/2 cable - there will be two colors, one black and one white. Wrap a couple of turns of black tape on the white wire both at the heater location and on the white in the panelbox. connect the 12/2 to your 2 pole breaker, the black wire and the taped white to the breaker.
Posted on Sep 06, 2007
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Mar 07, 2014 | Ouellet Heating & Cooling
Nov 30, 2013 | Coleman Propane Forced Air Heater...
Nov 04, 2013 | Heating & Cooling
Oct 19, 2013 | Coleman Heating & Cooling
Feb 03, 2013 | Dryers
Jan 26, 2013 | Computers & Internet
Sep 16, 2011 | Speed Ceiling Fan 3-speed Switch By...
Jul 09, 2011 | Leviton 1755 Triple Rocker Switch Decora
Nov 07, 2010 | Cadet Manufacturing Hot One® RCP502S...
Aug 11, 2017 | Fahrenheat FFH1615 Heater
Dec 22, 2017 | Fahrenheat FFH1615 Heater
429 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: