Question about Haier HPAC9M Air Conditioner
Check if the condensar ( outside fan unit) is getting enough free ventilation. IF there is no free air flow you will mostlikely be triping the unit due to short cycling. Ie the unit is pulling its own discherge air causing the compressor to trip due to high back pressure
Posted on Sep 07, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 17, 2016 | Frigidaire FAS256R2A 25,000 BTU Window Air...
Feb 09, 2012 | Frigidaire Refrigerators
Jan 29, 2012 | Magic Chef MCBR445B2 (4.4 cu. ft.) Compact...
Aug 22, 2010 | Dometic Rooftop RV Air Conditioner
Jul 22, 2009 | Heating & Cooling
May 19, 2009 | LG Heat cool Window Air Conditioner
Apr 05, 2008 | Refrigerators
Jan 05, 2008 | Kenmore 73089 Air Conditioner
410 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: