Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Ths sounds like the outside unit or compressor is not kicking in, check for power to the unit at the breaker box, or at the bottom of the contacts!
Posted on Sep 13, 2008
Check outside unit if unit and compressor are running feel the large line to see if it is cold. If compressor is running and line is not cold possible charge problems. You may have a capacitor problem outside. they go out quite often. You can change this yourself, Open up outside unit and the cap is the silver bullet with terminals out the top. Bad cap can cause compressor to not operate and also the fan. You need to clean the coil inside or at leat check the coil to see if it is clean. You can clean theis with a toilet brush do not go against the coil bit brush with the fins. You may need to call a service tech but try these options first. russ
Posted on Aug 15, 2009
SOURCE: unit not cooling
Low on refrigerant charge! Low side line should be cold like a beer can at the inlet of the compressor with some sweat beads around it. 55deg. The discharge should be around 125deg just hot enough you cant hold it long!
Posted on Aug 29, 2010
SOURCE: My Goodman Central AC Unit
Hi, have you checked all breakers, fuses in the disconnect box at the outdoor unit as most have them in behind the pull out off plug. Please give me more information on this and I can solve this for you.
Posted on Sep 01, 2010
SOURCE: Goodman Central AC Model #
That is a high pressure safety switch....either the switch is bad or you are running extremely high pressure and need to unit serviced...you should hire a pro to find out the exact cause of your problem...gauges will need to be placed on the unit to determine that exact problem.
Posted on Jul 21, 2011
Tips for a great answer:
Sep 03, 2017 | Goodman Heating & Cooling
Jun 15, 2014 | Goodman Heating & Cooling
May 29, 2014 | Goodman Manufacturing GSZ130181A - 1.5 Ton...
May 10, 2017 | Goodman Heating & Cooling
Jul 11, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 23, 2011 | Goodman CKL42AR42 Air Conditioner
Feb 21, 2011 | Goodman CKL36AR36 Air Conditioner
Jun 20, 2009 | Heating & Cooling
Sep 13, 2008 | Goodman Heating & Cooling
44 people viewed this question
Usually answered in minutes!