Question about Sta Rite Pool & Spa
Water pressure. jump the pressure switch. if it runs then replace the switch. ensure proper waterflow from pump
Posted on Aug 07, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 21, 2015 | 1995 Chevrolet K2500
Dec 29, 2011 | Whirlpool Stove Oven Sensor 8053344
Jun 16, 2011 | 1997 Honda Accord
Jun 08, 2011 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
May 10, 2011 | Maytag MER6772 Gemini Electric Kitchen...
Here is the reason for that problem per the manufaturers web-site
The low-pressure switch senses the refrigerant pressure in the sealed refrigeration system to
protect against certain conditions that could be detrimental to compressor life. The switch shuts
the unit down in the event of loss of refrigerant, fan motor failure, evaporator freeze-up and
airflow blockage. The switch automatically resets when the pressure rises to normal operating
pressures. The display will show "LP" if this switch is tripped.
The low-pressure switch will shut the heat pump down when the evaporator starts to freeze.
When the unit starts to freeze the low-pressure switch will be tripped, causing the display to read
"LP" This will prevent the evaporator from becoming damaged or deformed.
If the air outside the heat pump is not warm enough to produce heat, the system will shut down.
The actual point at which your unit will shut down due to low temperature varies depending on
which model you purchased, current weather conditions, and the amount of sunlight reaching the
heat pump. The shutdown can occur anywhere within a wide range of temperatures, usually 45°F-
55°F. This is not a "fixed" range. We stress that climate conditions, sunlight, and various models
respond quite differently to low ambient temperature. A shutdown occurs because low
temperatures will activate the systems low-pressure safeguard switch (digital thermostats will
display a code "LP".) The unit will start up again when the temperature has raised enough to reset
this switch. Note: Low ambient temperature does not necessarily affect the Chiller models
or the cooling cycle of the heat/cool units.
If this post has helped you, please take the time to vote positively for me on this site. If you need additional help, I can be reached @: firstname.lastname@example.org
Oct 23, 2010 | Hayward Heatpro 81k Btu Swimming Pool Heat...
Oct 13, 2010 | Computers & Internet
Jun 30, 2009 | 2002 Chevrolet TrailBlazer
Aug 30, 2008 | SkyScan 86742 Digital Atomic Wall Clock
29 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: