Question about Zinsco GTE Sylvania Electrical Supplies
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: gfci breaker for spa
gfci's are designed to trip if they receive voltage on there ground/neutral side, therefore my vote is for Smithbrother I would say there is probably a partial short somewhere in you system.
Posted on Mar 24, 2009
yes. If you still have the fault it will not reset. Disconnect the out going wire to isolate the breaker and try again. If it still doesn't reset then the GFCI breaker is bad and needs to be replaced. Hope this helps you, Jeepfxr
Posted on Jan 28, 2010
There are literally dozens of brand options on the market. All are to specified standards. Contact any electrical supplier to obtain one for your system.
Please rate my help++++Thyanks for using fixya
Posted on Mar 21, 2010
You can buy an inexpensive GFCI tester for as little as $10-$12. A better one with several mv settings will cost you a bit more. This way you can test this circuit and even GFCI receptacles. Then you'll know for sure if your breaker is working.
Posted on Nov 15, 2010
If you have a Bryant load center, you can use other breakers in it, including the Eaton GFCB120 GFI since several companies unified their design. The GFI (ground fault interrupter) or GFCI (ground fault circuit interrupter), same thing, may be required for a device you are installing, such as bathroom, kitchen or outdoor fixtures.
The Eaton series includes very clear installation instructions, but if your problem is that they are missing, then all you do is install the breaker in a open slot in the breaker panel, but you have to attach the neutral [white] wire differently. On regular breakers, the neutral goes right to the ground lug in the panel. With a GFI breaker, it goes through the breaker, and then is connected to the ground lug.
Posted on Mar 20, 2012
Tips for a great answer:
Aug 01, 2013 | Sylvania Electrical Supplies
Nov 29, 2012 | Sylvania Electrical Supplies
Jun 17, 2011 | Leviton R01-7299-0NI Switch And GFCI...
Nov 14, 2010 | General Electric 20 Amp, 1 Pole Thick Type...
Jun 24, 2010 | Solar 15 Amp Murray Afci Circuit Breaker
Mar 26, 2010 | Sylvania Circuit Breaker - Zinsco/ 50 Amp...
Dec 05, 2009 | Amana ARB2257C Bottom Freezer Refrigerator
May 13, 2009 | GE GTS22KBP Top Freezer Refrigerator
Dec 17, 2008 | Prime 10 Amp Circuit Breaker
299 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: