Question about Heating & Cooling
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Brivis Wombat ducted heater:
This is most likely the thermocouple. Before you come to the conclusion you have to change it... make sure the mating area at the gas valve is clean. Disconnect the thermocouple mounting nut and clean both the end of the thermoouple and the area where the thermocouple is mated to the gas valve. Additionally make sure the flame passes over at least 1/4 inch or more of the thermocouple probe end. Reposition as necessary to make it rest in the flame. If you have to bend it... do so very slowly and carefully. It is better to bend the bracket vs the thermocuple if possible.
The would be rare but it is possible that you have a very good vent / flue for your heater and the wind is creating a venturi effect that causes too much flue air flow. Maybe 2 times in 40 years I have seen this. It took some careful modifications to the flue cap on the roof by riveting some extra metal pieces on to the cap. (trial and error for over an hour!!!) I seriously doubt this is your problem.
You either have a dirty thermocouple
Dirty thermocouple mating area
Inproperly positioned thermocouple
or.... of course the thermocouple is just slowly failing.
I do NOT think you have a gas valve problem at all.
Thanks for choosing FixYa,
My experience: http://blog.fixya.com/index.php/2010/05/award-winning-service
Posted on Jul 03, 2011
Tips for a great answer:
May 04, 2018 | Heating & Cooling
Aug 24, 2014 | Heating & Cooling
Aug 08, 2011 | Heating & Cooling
Jul 15, 2011 | Heating & Cooling
Mar 26, 2011 | Heating & Cooling
May 12, 2009 | Heating & Cooling
Jul 22, 2018 | Thermostats Heating & Cooling
Jul 21, 2018 | Heating & Cooling
60 people viewed this question
Usually answered in minutes!