Question about Raypak Versa 130,000 Btu Above Ground Natural Gas Heater
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
ILO or ROL. There is no EOL.
ROL is a switch inside the lower left corner of the heater. Press the red button. ILO is a lockout. Power down and power up.
Posted on Dec 21, 2008
this usually indicates a high limit condition.you must first ascertain if you have a component failure or a true high tempature condition.your model has 2 limit controls and they are both located in side panel on water in/out header
Posted on Sep 19, 2009
There may be a buildup of carbon on your pilot or your gas pressure may be low. It is hard to say without more info on the heater, gas line size and meter size. Depending on where you live it could also be something like spider webs in your gas orfaces. These will cause all to fire normally but not be consistant enough to read fire back to the ignition control. A small piece of bent wire into the orfaces will help to clear this up. As it is not a heater related problem it will not show a ready made answer on the display. Hope this helps, let me know.
Posted on Nov 07, 2009
SOURCE: service code ROL
This indicates the flame roll out safety switch is bad. This part is usually mounted right above the burner tray. It is a white ceramic piece with two wiring terminals and an external part that looks like a resistor. This part detects flame/heat coming out from the burner tray. When replacing it, be sure to check for blockage at the burner tray, heat exchanger and the flue if vented with duct work. This is a critical safety device so do not bypass it.
Posted on Jun 19, 2010
Tips for a great answer:
Aug 11, 2014 | Raypak 130,000 BTU Propane Gas Pool...
Apr 29, 2014 | Raypak Pool & Spa
Jul 31, 2013 | Raypak Pool & Spa
Mar 02, 2013 | Raypak 199500 Btu Digital Natural Gas Pool...
May 21, 2012 | Raypak 266A Digital ASME Natural Gas IID...
Sep 05, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Jun 19, 2009 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
44 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: