Question about Goodman Heating & Cooling
Most likely cause is the dual capacitor for compressor and fan is bad.
Posted on Oct 27, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Sounds like a bad capacitor. They can be bad and the fan will still run. Turn off power and check for burnt wires on the top of the contactor going to the capacitor or on the top of the capacitor.. Check terminals on the compressor also. When capacitors go bad they are slightly swollen. They can also look good and be bad . Could be compressor but start with capacitir and wires. IWork on a lot goodman units. Most of the time it is the cap.
Posted on Jun 03, 2009
are you speaking of the outside fan or inside? compressor should be a little warm but not boiling hot. the unit could be low on freon. if low it will run a while but the compressor will overheat and shut off leaving the fan running by itself ouside. if nothing outside is running check power. if you have power check the contacted outside to make sure it's pulled in. contacters are bad about going out on goodman untis. Also ants can get under contacts.
Posted on Jun 18, 2009
Tips for a great answer:
May 07, 2016 | Goodman Heating & Cooling
Aug 28, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 27, 2010 | Goodman CKL60AR60 Air Conditioner
Sep 11, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 22, 2009 | Goodman Heating & Cooling
May 15, 2009 | Goodman CKL60AR60 Air Conditioner
115 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: