Question about Raypak Pool & Spa
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: service code ROL
This indicates the flame roll out safety switch is bad. This part is usually mounted right above the burner tray. It is a white ceramic piece with two wiring terminals and an external part that looks like a resistor. This part detects flame/heat coming out from the burner tray. When replacing it, be sure to check for blockage at the burner tray, heat exchanger and the flue if vented with duct work. This is a critical safety device so do not bypass it.
Posted on Jun 19, 2010
Tips for a great answer:
Jun 02, 2015 | Raypak 266A Digital ASME Natural Gas IID...
May 21, 2012 | Raypak 266A Digital ASME Natural Gas IID...
May 14, 2012 | Raypak 266K BTU Digital Residential...
Jun 29, 2010 | Pool & Spa
May 29, 2010 | Raypak 130,000 BTU Propane Gas Pool...
114 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: