Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: my LG Artcool isn't working
CH61 means Condenser coil temp high due to non cleaning of condenser/over charged gas/non condensable gas.
Clean your condenser coil. If still problem rests, due to non condensable gas also there will be high temp. kHnce remove the gas, flush out the system and vacumize and then do gas charging.
Posted on Dec 10, 2010
Indoor unit return air sensor fault, Open or Short. Disconnect sensor from PCB and measure resistance. 8 kOhm at 30C and 13 kOhm at 20C if not replace sensor.
Posted on Jan 01, 2011
SOURCE: LG Artcool about 4 yrs
CH 5 on these machines indicates a communications error between the indoor and outdoor units. Generally, it will require a replacement outdoor board assy to repair it. Lookup LG parts on the internet or ring them for your nearest Agent or parts stockist.
Posted on Jun 16, 2011
Tips for a great answer:
Feb 14, 2015 | Carrier Heating & Cooling
Aug 31, 2011 | LG Art Cool LA121CNP wall/window Air...
Jun 16, 2011 | Heating & Cooling
Apr 14, 2011 | LG LHD45EL Dehumidifier
Dec 10, 2010 | LG Heating & Cooling
Aug 08, 2009 | LG LHD45EL Dehumidifier
Jun 26, 2009 | Comfort-Aire BHD-501 Dehumidifier
Jan 29, 2009 | Sharp AR-160 Copier
Jan 14, 2009 | LG LSC183VMA Split System Air Conditioner
14 people viewed this question
Usually answered in minutes!