Question about Heating & Cooling
I have a Goodman CPLE24-1C air conditioner that is remotely connected to a Janitrol AR24-1 (Goodman HKR-05) air handler. The unit cools very well for the first 30 to 45 minutes. Then it starts sending hot air out the air vents and the fan on the outside unit moves very slowly and the outside unit is hot enough to burn you if you touch it. Any ideas? Thanks Mark
Hi, Could be a run capacitor on the fan motor. They usually swell up and or leak when they go bad. If not, the only real way to test them it with a specific capacitor tester. A new capacitor would be cheaper. Make sure that the outside unit is disconnected from power before opening it up, try to spin the fan blade by hand. If it doesn't spin freely it may need oiled if possible. See above solution. Your problem is the fan motor though so if this don't do it, It will have to be replaced. If this helps, Please rate my solution. Thanks, kstfas
Posted on Aug 31, 2007
It appears the nuetral wire or improper grounding if its 120V unit. 220v unit will be a loose phase off of line one or two in panel box or unit connection. If this problem is common between other units it will be a factory design problem allow a single phase simulation to occur. Loss off phase would cause motor to slow down and overheat. Once outside unit is not functioning correctly where the outside condensor is not removing the heat through the condensor, you will get hot air through the inside mini split system.
Posted on Oct 30, 2008
Try this. Turn off the system and remove and inspect the air filter in the air handler for a restriction. If you find no restriction, go outside and turn off the outside unit by shutting off the disconnect switch. Turn on the system and keep the inside unit blowing for 3 hours. Then go back outside and switch on the outside unit. If the air conditioner blows cold air again it means that the inside coil is freezing up due to lack of refrigerant or something else. The slow moving outside fan could indicate that it is bound up and going off on thermal overload. Listen to see if the motor makes a moaning sound. Lubricate it if you can get to any of the oil holes in located in the end caps of the motor. At any rate you may need to call a technician. Good Luck
Posted on Aug 31, 2007
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 26, 2015 | Goodman Heating & Cooling
Jul 24, 2014 | Goodman Manufacturing Goodman MSG18CWN1W...
Nov 09, 2013 | Heating & Cooling
Feb 15, 2013 | Goodman Manufacturing Goodman GSC130181...
Mar 19, 2010 | Goodman CKL42AR42 Air Conditioner
Dec 18, 2009 | Goodman CKL49AR49 Air Conditioner
Jun 23, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 14, 2009 | Goodman CLQ36AR49 Air Conditioner
Feb 16, 2009 | Goodman PHKJ048-1 Air Conditioner
First turn the main power off to the unit at the breaker, wait about five min. and switch the breaker back on, then see if this solves the problem. In the instalation manual that came with the unit on the last page you will see a code of the red blinking light, this will tell you the most likely problem if not solved by switching the breaker on again.............Hope this helps
Oct 14, 2007 | Hitachi RAS-09UH Air Conditioner
585 people viewed this question
Usually answered in minutes!