Question about Heating & Cooling
Have changed battery
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Rinnai Econoheat 850 gas heater
It needs a service. The jets carbon up and when they heat up they stop the gas getting through. If you take it to a Gas Shop they will charge you around 90-00 to service it and all they will do is blow it out with compressed air. If you can get hold of an Air Compressor with an Air Blower on the end you can blow it out yourself. Remove the Gas Hose from the back and place the Air Blower into the hole where the gas goes through and hold down the ignitor switch to open up the jets. Give it a good blow out. Once you have done that give the candles a blow as they eget dirty also. You will see a white dust more than likely come out of them. If you want to give it a good clean out remove the cowling and clean (blow out) the inside of the Heater. The cowling from memory has only about 6 or 8 screws holding it on. That should take the top and sides off. I can't remember if you can remove the lower vent on that model - if so it will only be either 2 or 4 screws. Hope this Helps.
Posted on Jun 21, 2008
SOURCE: rinnai econoheat 850
sounds like it has a faulty button. The "on" button on that model has a button on the front side which should hold the on button down after igniting. Check and make sure that it is there. I think it is a spring loaded button - maybe the spring has dis-lodged itself. If the button is faulty yhou can only replace it.
Hope this Helps
Posted on May 22, 2009
The thermocouple [s] require replacement, or in my experience try servicing the unit first. There is an injector for the main pilot and a secondary injector for the flame thrower ignition. Both of these are prone to blocking due to dust and can be enough to shut the unit down. Although usually this is thermocouple related as you are manually keeping the unit running when you hold down the button, if the tcouple is broken it wont send enough millivolts to hold the magnetic valve open when you release the button.
Posted on May 31, 2009
Normally purple/blue on the radiants indicates low gas pressure, could also be dust slowing gas velocity into burner and/or an aeration problem. Get it checked out properly.
Posted on Jul 19, 2009
Tips for a great answer:
Jan 16, 2017 | Camping, Backpacking & Hiking
Jul 24, 2016 | Rinnai Heating & Cooling
Nov 02, 2015 | Grilling
Apr 08, 2015 | Weber Grilling
Feb 25, 2010 | GE JGBP28 Gas Kitchen Range
May 16, 2009 | Rinnai Heating & Cooling
May 15, 2009 | Heating & Cooling
Jun 17, 2008 | Heating & Cooling
19 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: