Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: E1 error code
highly annoying issue error code E1. After hours
of fan operation, the error code E1 will appear on the seven segment
LED temperature display. This error code is intended as a reminder for
the user to clean the air filter. However, because the procedure
outlined in the user manual does not clear this error code as
indicated, and the appliance has a nonvolatile memory that cannot be
reset by simply unplugging it, the user of the appliance will become
mightily frustrated, standing in potentially sweltering heat watching
the appliance repeatedly shut down in the midst of operation with the
"E1" display flashing.
Believe it or not, that is what it does: if you unplug it to remove the
"E1" code from the display, and plug it back in and re-start it, it
will simply run for anywhere from a few minutes to a few hours, and
then merrily shut down again with the same flashing "E1" code.
So you will come home to a hot bedroom, living room, etc. unexpectedly,
and you will NOT be amused, as I was not.
Many people at this point, having put the manual under the canary or
some such, will simply return the unit and never buy another Sharp air
conditioner. But for the tech-savvy and search-adept, I offer the
following procedure to clear the nefarious E1 indication, and obtain
1. Power down the air conditioner using the "power" button on the front
2. Unplug the air conditioner from the wall socket.
3. Hold the front panel "power" button down and plug the air
conditioner in. Continue to hold the power button down as the machine
goes through a brief test sequence (fan & compressor each come on
briefly, etc). There is a "beep" sound at the end of the test sequence,
and the machine will be off. At this point, you can release the power
4. Unplug the air conditioner.
5. Plug the air conditioner back in.
6. Congratulations! You should now be able to operate the air
conditioner normally for another 720 hours, but only if you followed
the instructions above EXACTLY.
Was this solution helpful? Show your Appreciation by rating it.
Thanks for using fixya support..You have a wonderful day
Posted on Jun 05, 2008
I had the same problem and found a fairly simple solution. UNPLUG THE UNIT FIRST. All left and right reference below is as view from the BACK of the unit (NOT from the front). Open the right side panel (right as view from the back), by removing six screws (remove screw covers first) and pull down on the panel to remove. Towards the UPPER-back of the unit, there is a cold air evaporator(?)(bunch of tubes and fins) you can only see the edge of it after removing the right panel. Below it is a white plastic drip tray with a hole at the end allowing water to pass down to the lower warm air radiator(?) (another bunch of tubes and fins) to evaporate. If this hole is obstructed, water will over flow and leak. I cleaned out the hole with a vacuum attached to a drinking straw, you might have a better way. After cleaning, I poured a little water through to make sure it drains. There is a lower drip tray at the bottom of the unit which catches the water and you can drain it out the bottom drain hole by unplugging the rubber stopper at the back bottom of the unit. The lower drip tray has a float switch (you can only see it by removing the back panel, which you don't have to do for this procedure) which turns off the unit when the lower tray is full. So, theoretically, even if the evaporation is not working properly, as long as the upper drain hole is not obstructed, there should not be any leakage, because the water will drain into the lower drip tray and turn the unit off when it is full. The upper drain hole obstruction might be causing most of the leakage problem. Also make sure the unit is level left to right. If the left side (left as viewed from the back) is lower than the right side (as view from the back) the water in the upper drip tray might not flow to the drain hole properly and might overflow. You should also vacuum and clean the upper plastis filter screen (pull it out from the top back of the unit). Before closing the right side panel, you might want to vacuum and clean the lower warm air radiator, be careful not to damage the fins. Again before you start any of this, UNPLUG THE UNIT FIRST. This might be easier than packing and sending the over 90 pounds unit to an out of town service center. I understand some service centers might charge $100 for a simple cleaning. Consult a trained technician if you don't have the skill to do this. Do this procedure at your own risk because I am not sure if it might void you warranty. Again UNPLUG THE UNIT FIRST before you start.
Posted on Feb 23, 2009
Tips for a great answer:
Feb 07, 2015 | DeLonghi PAC85 Pinguino Portable Air...
Nov 12, 2014 | Heating & Cooling
Aug 19, 2014 | Heating & Cooling
Jul 17, 2012 | DeLonghi PAC W130 Portable Air Conditioner
Nov 28, 2011 | DeLonghi PAC T110P 11000 BTU Portable Air...
Jul 29, 2009 | DeLonghi Pinguino PAC-290 Air Conditioner
Feb 03, 2009 | DeLonghi Pinguino PAC-02 Air Conditioner
Jun 05, 2008 | DeLonghi Pinguino PACL90 Portable Air...
Aug 21, 2017 | Heating & Cooling
68 people viewed this question
Usually answered in minutes!