Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
If it were me I would use an amp meter and take an amp reading of the compressor when it is fully loaded. then I would refer to my name plat. which should be located on unit or if you can read label on compressor that is even better. FLA is fully loaded amps. RLA is running load amps, and LRA is locked rotor amps. if your amp readings is close to LRA or higher than FLA then I would recommend changing your compressor, The last thing you want is a compressor burn out.
Posted on Mar 09, 2013
Tips for a great answer:
Jul 04, 2017 | Heating & Cooling
Jan 04, 2016 | Heating & Cooling
Aug 08, 2015 | LG Heating & Cooling
Sep 03, 2014 | Amana PTC124E50AXXX
Jul 29, 2014 | Islandaire EZ4212B2C1S45AA 12000 BTU Class...
Mar 08, 2013 | Heating & Cooling
Jul 08, 2012 | Amana Ptac Heat Pump Control Board Kit...
Jan 28, 2010 | Heating & Cooling
116 people viewed this question
Usually answered in minutes!