Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: LG split (3 indoor) LMU360CE
The LED #2 is only flashing while in disconnection or short in Thermistor (3 sec off / 0.5 sec on). If you want to change it, note: this is not an easy job to do! You will need to remove the top panel, then remove the control paneland then the front panel to gain access to the thermistor. The part isnot available to the public and requires an authorized service techfrom LG to take care of this problem. You will need a special tool toremove the front door seal spring clamp.
But you can call customer service @ 800 243 000 and see if theycan transfer you over to parts. Just give them the model and serial #and see if they would be willing to sell you the thermistor part. Youwill also need the door seal spring clamp removal tool to make the jobeasier.
Posted on Aug 02, 2009
E-5 -Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 03, 2011
SOURCE: hi there, we had blackout
E-6 Indoor/outdoor transmission error. error.
Comms Error, check your wiring, remove external pumps. Split/Multi - check volts from terminal N to 3 = 0 - 65 Vdc, Multi V - 4 Vdc terminals 3 and 4
Posted on Jan 23, 2011
SOURCE: im getting an E6 error
Check your low voltage wires they are easily damaged. I have seen weed eaters cut the wires rodents you name it. check the wires closley also check the furnace circuit board check the 3 amp fuse it looks like a car fuse. if thew fuse is blown on circuit board your contactor at the A/C unit is probably bad. If this help please rate me and do a testimonial.
Posted on May 20, 2011
Tips for a great answer:
May 03, 2016 | Heating & Cooling
Jan 01, 2016 | DeLonghi Heating & Cooling
Mar 19, 2014 | Heating & Cooling
Aug 01, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Jan 23, 2011 | Heating & Cooling
Jan 04, 2011 | Mitsubishi Heating & Cooling
Dec 05, 2010 | Mitsubishi MS12TN Air Conditioner
200 people viewed this question
Usually answered in minutes!