Question about American Standard WCZ036F Air Conditioner
Not sure if you ever figured it out. Or if someone figured it out for you. Shows no one answered you on here. So I thought I would ask you a question plus also say what I thought it was . When the unit and or the thermostat was replaced? Was the thermostat wire that is inbetween the unit and the blower ever replaced? A service tech should have checked if the tstat wires were touching or shorted together. If you go by color which you should never do. Red is usually 24 volts or power, green is fan, yellow is cooling, white is heat, orange is the reversing valve if its a heat pump, orange to O terminal if RV in cooling or orange to B terminal if RV in heat. O or B terminal depends on who the manufacturer of the unit is. Blue wire is usually the common. you should always check to see how it is wired at the board or relay in the unit. not everyone wires it by the colors. If your fans low voltage wires are touching the low voltage 24 volt power wires in the unit or if the wires are shorted or touching in the wire sleeve or at the thermostat. the blower motor will never shut off. Or if the blower motor is wired directly to line voltage it will never shut off and testing the low voltage wire wont matter.
Your question was from last summer. So I am assuming you had someone figure it out by now. If not then check my suggestions. Hope that helps you.
Posted on Apr 02, 2014
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 09, 2017 | Dometic Heating & Cooling
Oct 01, 2015 | AC Cars & Trucks
May 31, 2012 | Heating & Cooling
Dec 30, 2011 | Heating & Cooling
May 13, 2011 | Ruud Heating & Cooling
Sep 21, 2010 | Heating & Cooling
Jun 18, 2010 | Goodman CKL36AR36 Air Conditioner
Jul 13, 2009 | Ruud UAKA060 Air Conditioner
Apr 25, 2009 | Heating & Cooling
Aug 11, 2008 | LG LS-L1210CL Mini Split Air Conditioner
53 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: