Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
A basic model heat pump with an air handler with electric strip heat generally will continue to run with a call for heat regardless of the outdoor air temperature unless there was an outdoor thermostat (an accessory) installed. There is still heat in the outdoor even at temperatures of zero and below. Generally, there is a balance point of approx 30-35degF that allows the heat pump to heat your house to 68degF without the need for the electric heaters. Below that, the heat pump can still extract heat from outside and "pump" it into your house; however, it will need help from the electric heaters. In temperatures below the balance point, the heat pump will run non-stop. As the temperature in the house falls approx 1 - 2 degF below the setpoint, the electric heaters will energize. So it is not uncommon for the system to run non-stop with the temperature falling a few degrees below setpoint. The colder the outside temperature, the more often the strip heaters will cycle on/off. If your system is well-maintained and operating at proper performance, it is still cheaper to run your heat pump than it is to run on straight electric heat. If you live in a climate where below zero temperatures are normal during the winter months, you might want to research heat pump options that offer higher COP's and increased performance in colder temperature than the basic contractor's model. Start with initiating communication with a local contractor. You will need to consider initial cost and the pay-back period based on your local energy costs and your specific demands you want your system to meet.
Hope this helps!
Posted on Feb 14, 2010
Tips for a great answer:
Jan 19, 2018 | Water Water Heaters
Mar 08, 2015 | Carrier Humidifiers
Feb 11, 2015 | Carrier 52CE215 Cool Electric Heat Air...
May 29, 2017 | Carrier New 5 Ton Ground Source Geothermal...
Jan 27, 2013 | Carrier Heating & Cooling
Jan 05, 2012 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 28, 2011 | Carrier XHC101D Air Conditioner
Feb 14, 2010 | Carrier 38CKC036 Air Conditioner
Aug 27, 2008 | Saunacore Special Edition Residential...
58 people viewed this question
Usually answered in minutes!