Question about LG LAN240HSV2-LAU240HSV2 24000 BTU 20 SEER Art Cool Ductless Heat Pump Air Conditioner
Sounds like it could be low on freon I believe these units have about 1.5 pounds of freon in them and are critical in not undercharging or overcharging them if it is a freon 410 ac unit the pressures should be about 135 and both lines cold if is low on freon a service tec will need to be called to try to repair the leak if possiable
Posted on Jul 21, 2013
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Remove the front cover of the unit to expose the cooling coil. Put the unit on and observe if there will be formation of frost (ice) on the coil. If there's frost formation, the common cause is dirty cooling coil. Have it cleaned using an alkali base coil cleaner. If the coil is clean, then the problem is the fan motor. It might be turning slow due to copper loss. Have it replaced.
Posted on May 29, 2009
please check the temperature sensor this will make the compressor for running and stopping and also check the compressor if its in warranty period please call the service technician to check these and replace if necessary.
Posted on Sep 04, 2009
my window ac 1.5ton cut off with a **** at 28 deg temp with in 3 minute .room temp is 31 deg. ac is 2years old and i bring in good working condition from my brother. it was kept idle for 1 year
Posted on May 09, 2010
Tips for a great answer:
Aug 15, 2016 | Heating & Cooling
May 09, 2016 | Frigidaire Heating & Cooling
Jan 10, 2015 | Emerson 1F89EZ-0251 Blue 2" Thermostat,...
Dec 25, 2014 | Heating & Cooling
Dec 19, 2010 | Goodman PHKJ024-1 Air Conditioner
May 27, 2010 | Kenmore Single Room Air Conditioner
Oct 12, 2009 | Heating & Cooling
May 03, 2009 | Movincool Office Pro 36 Portable Air...
Jun 10, 2008 | Heating & Cooling
Oct 31, 2006 | Mitsubishi MS12TN Air Conditioner
202 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: