Question about Heating & Cooling
Need to know how to wire in a new capacitor, and quick start unit. Have disconnected wires and need to kmnow where they go back onto clips Model ACO24M1O2ICG. Thanks
Can you post a pic of the unit s electrical opened up here and I amy be able to step you through it
Posted on Jul 21, 2013
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Here is the standard connection of dual capacitor. Actually you can see the diagram on the unit but Im not familiar with the Intertherm model. What can I give to you is only the standard connection of dual capacitor.
Posted on Feb 26, 2008
Is the blower wheel turning? Did you by chance have to remove the motor from the blower wheel to work on it? If you did, did you put the blower wheel back on in the correct direction of air flow? Also, did you put the correct capacitor back on the unit so it can get up to the required rpm's? These are things that you will need to check for. If the motor is running and the blower wheel isn't and the wheel is tight on the shaft, then you will have to replace the motor. The brushes may be bad on the unit and it's not turning the shaft. Hope these ideas help.
Posted on Apr 10, 2009
SOURCE: rewire air conditioner controls
Assuming "Window Unit" with rotary switch.
L1 (smooth part of line cord) to thermostat 1, thermostat 2 to overload (black disk) from overload to Common( C) terminal on compressor.
From Run (R) terminal on Compressor to Common (C) terminal on dual capacitor. From Start (S) terminal on Compressor to "Herm" terminal on capacitor. From fan motor to # 4 on switch = Medium Speed, to # 6 on switch = High Speed, from fan motor to # 7 on switch - Low Speed. Brown wire from fan motor to (F) on dual capacitor, white wire from fan to (C) on capacitor and L2 (ribbedwire) (N) to (C) on capacitor
Posted on May 10, 2009
I think the wiring diagram is on a printed sticker on the side of the water collector, just pull it out of the right side as you look at it. There should be one on there hope this helps as i have the same unit in the other room. regards Richard
Posted on May 29, 2009
Tips for a great answer:
Aug 06, 2014 | Heating & Cooling
Oct 04, 2012 | Goodman GPC1342H21A Air Conditioner
Oct 03, 2012 | Heating & Cooling
Aug 08, 2010 | Ruud UBHC Air Conditioner
Aug 02, 2010 | Heating & Cooling
Aug 30, 2009 | Coleman Mach III Air Conditioner
Aug 27, 2009 | Heating & Cooling
Aug 07, 2009 | Heating & Cooling
Jun 26, 2009 | Dometic Rooftop RV Air Conditioner
May 10, 2009 | Heating & Cooling
Oct 18, 2017 | Heating & Cooling
94 people viewed this question
Usually answered in minutes!