Question about Heating & Cooling
American- Carrier flashing ERROR code 2 and wont come on
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: My Heat will not work
the e2 code on a carrier comfort zone thermostat is indicitive of the external safety sensors which are located on your units ductwork in the attic. the e2 code are the hpt/ and lat sensor codes. the hpt is the heat pump temperature sensor and the lat is the leaving air temperature sensor. you can pull off the cover of the panel and behind it will actually give you all the fault codes associated with you carrier tsat.each sensor has a certain ohm rating and if its out of the range it will fail. now as to the reasons for failure, the indoor coil could be dirty, filters dirty, refrigerant charge incorrect.
Posted on Dec 22, 2008
the e2 error on your thermostat is a problem with the return temp sensor on your system, the only thing you can really do is call a company and replace it, you can't bypass it or remove it cause the system wont run properly
Posted on Jun 30, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
SOURCE: I have error codes flashing
Error codes from American Standard Pub 18-HD32D2-8, which is a one-sheet document that came with my American Standard air-conditioner:
29 = not listed
129 = not listed
80 = HPCO Fault - problem is in outdoor unit - Desscription: High Pressure Monitor Fault (hard lock out, cycle power to reset)
91 = Communication Inactive Fault - problem is in air handler - Descriptions - COMM Bit Master Clock Error, COMM Heat/Cool Demand Error, Serial Motor Communication Inactive Error
91 = Communication Fault - problem is in furnace - Descriptions: Blower motor no COMM response, Inducer motor no COMM response, Loss of heat/cool demand, Loss of clock signal
91 = Communication Fault - problem is in outdoor unit - Descriptions: Loss of Heat/Cool Demand Message (COMM), Loss of Bit Master (Clock Signal)
91 = Communication Fault - Description: Comm line is dead and no bits have been received.
By the way, I do not recommend American Standard. I've had mine 14 months and it just blew up - the entire control panel blew. My advice to you - think about a different brand.
Posted on Sep 21, 2010
Tips for a great answer:
Jul 24, 2015 | American Standard 5000 Heat Pump Unit
Jul 21, 2015 | Canon PC-920 Black and White Copier
Feb 14, 2015 | Carrier Heating & Cooling
Mar 05, 2014 | Carrier Totaline P291-1003 Capacitor 10mfd...
Apr 23, 2012 | Exercise & Fitness
Nov 22, 2009 | Carrier TSTATHCP Programmable Thermostat...
Sep 10, 2009 | Office Equipment & Supplies
Jun 29, 2009 | Carrier 38CKC060 Air Conditioner
Jun 24, 2009 | Carrier 38CKC060 Air Conditioner
Dec 03, 2008 | Carrier Heating & Cooling
93 people viewed this question
Usually answered in minutes!