Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Amana PTAC
Sounds like if this is a heat pump, maybe it tripped out on high pressure. Maybe just unplugging the system may reset the control boards. This maybe due to a dirty filter or dirty evaporator coil.
Posted on Nov 18, 2007
The reset button is located behing a panel on the front of the unit that is labeled Heat Reset. If that label is gone then look around, it is a small hole, small enough for a paper clip to fit through.
That being said, I have 137 of these units in one of my hotels and have not had a single one needing to be reset. You probably are going to need a new control board kit. These can be purchased from Amana. They are $130. Make sure that you have pulled the heater coil out and inspected it first. Also, there was a recall years ago where Amana was supposed to contact and send out new voltage switches. These are the round black things that the Brown heater wires connect to on the upper and lower side of the heating coil. You should also try to replace those if you find the coil in good condition. I have had those resolve heating issues. Most of the heating issues were a result of a bad relay on the control board though.
Please remember to rate this fix.
Posted on Feb 12, 2009
Tips for a great answer:
Jan 12, 2018 | Amana Heating & Cooling
Sep 11, 2016 | Amana Heating & Cooling
Feb 19, 2015 | Amana DS01E - DigiStat Thermostat with...
Feb 02, 2013 | Amana In Wall Install Kit For Digismart...
Jun 19, 2010 | Amana PTH093B35AM Thru-Wall/Window Air...
Mar 26, 2010 | Amana PTH123B50AJ Heat Pump,12000BTU,...
Jan 28, 2010 | Heating & Cooling
808 people viewed this question
Usually answered in minutes!