Question about Heating & Cooling
Sticker on contactor is worn and cannot read part # or anything else on it contacts are corroded and filled with small ant bodies...thus preventing proper contact, and non-operation of the compressor and fan. need contactor part number to replace contactor.
What supplier do you have ? SQUARE D. +SIEMENS+TELEMECANIQUE?
God bless you
Posted on Jul 21, 2013
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check your wiring between the contactor and compressor for a short to ground, or check the compressor windings for short to ground.
With the Tstat off, the contactor should be open so the only way for the compressor to be trying to do anything is if the 110 volts from the unbroken side are traveling through the compressor to ground. Since 110v is not enough to run it, the overload is kicking it out, cooling off, and repeating the cycle. When you kick on the Tstat, the contactor is supplying voltage directly to ground without going through the resistence of the compressor windings and kicking the breaker.
Post back and let me know what you find.
Posted on Nov 20, 2007
SOURCE: replace contactor
On single phase your incoming power lines go to L-1 & L-2, the lines to the compressor go to T-1 & T-2. With A/C current it does not matter which one goes to which side as long as the line goes to the L side and the compressor power lines go to the T side. As long as the coil voltage is correct any contactor will replace the original.
Posted on May 29, 2008
SOURCE: High Pressure cutoff
YOUR OUTDOOR FAN MOTOR SHOULD NEVER SHUT OFF IN THE AC MODE. IT IS SUPPOSED TO SHUT OFF IN THE HEAT MODE WHEN ITS IN DEFROST. IF THE UNIT IS RUNNING IN COOL AND THE OUTSIDE MOTOR QUITS ,THE COMPRESSOR WILL QUIT SOON AFTER. EITHER THE RUN CAPACITOR FOR THE FAN IS BAD OR THE FAN MOTOR ITSELF IS BAD, IF CAP IS GOOD THEN THE MOTOR IS At FAULT. THE OUTDOOR PRESSURE SWITCH CAN ALSO OPEN IF THE INDOOR FAN MOTOR FAILS IN HEAT OR THE FILTER IS PLUM NASTY in heat OR THE INDOOR COIL IS PLUGGED UP in heat.. THE PRESSURE SWITCH USUALLY TRIPS AT 400 TO 425 SO ITS WORKING CORRECTLY. YOU MAY BE CONFUSING THE ISSUE SAYING THAT THE AIR IS HOT AND COLD INSIDE. IT IS COLD WHEN AC IS RUNNING HOT WHEN HEAT PUMP IS RUNNING IN HEAT BUT ESSENTIALLY not cold or hot if compressor isn't running, but a lot of folks describe the lack of cold air as hot when the compressor isnt running. but it basically is warm or house air temp.you test the capacitor with a capacitor tester or take it to motor shop and let them test it. odds are its a 5 , 7.5 or a 10. it should test within 10 % of rated value . ask for a RESCUE brand replacement motor. they are great ,reversable etc.carefully oil and sand the motor shaft and note exactly where the blade was located in relation to the grill so you get it back just the same. usually they wire up black to a leg of 220 power. white to the other leg of 220 power. brown and brown with white stripe to the capacitor.you can also pull whole fan shroud assembly on some units and take whole thing to motor shop and let them test motor cap, replace and all you do is return to unit and connect two power leads,
Posted on Oct 26, 2008
You may have cottonwood on your compressor. Before you spend any money, do two things. Rinse off your compressor to clear any cottonwood, and check your filters, they may need to be replaced. Hope that helps!
Posted on Jun 24, 2009
Tips for a great answer:
Jun 22, 2014 | Ruud Matching Split Air Conditioner
Oct 24, 2013 | Ruud UAMB Air Conditioner
Sep 01, 2013 | Ruud Heating & Cooling
Jul 27, 2012 | Ruud UAMB Air Conditioner
Apr 08, 2010 | Ruud UAMB Air Conditioner
Jun 30, 2009 | Ruud UAMB Air Conditioner
Jun 27, 2009 | Ruud UAMB Air Conditioner
May 29, 2008 | Ruud Central System Air Conditioner
Apr 24, 2018 | Heating & Cooling
75 people viewed this question
Usually answered in minutes!