Question about Computers & Internet
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
This is Easy,
MGE software is exclusive to them, they do this so that in the event the UPS needs any work you have to use them for remedial work, the problem is because they hold the monopoly they charge through the roof for parts and labour. you will need a factory trained engineer to turn up with a laptop to switch off the "Maintenance Alarms" I have an engineer that has the Software and availabilty to parts and we are much cheaper than MGE direct.
if you need any UPS help contact Glenn Prince @ Adept Power Solutions Ltd 01264 326726 or go to website www.adeptpower.co.uk
Posted on May 13, 2010
try to check the fluid in the cooling system, if it's full. then try to check the sensor on the cooling cap, or maybe change the sensor. Hope this help.
ps: cooling liquid is not water ( buy it from mge, i forgot what's the name )
Posted on Dec 03, 2010
If this galaxy 3000 is of European Type ( that is having a radiator with coolant) , then after following proper BYPASS/Shutdown procedures, you could level the coolant in the radiator. You may require the tool kit that the supplier normally supply for this type of job.Generally the design was such that no evaporation could occur, however at times the top up is required. It may be as little as 20 (millilitre) Please check also the cooling fan just below the capacitor assembly. I hope this will help
Posted on Jun 11, 2011
No you don't have to reconfigure the UPS after battery replacement. However you may have to reset the battery Timer. There are 4 possible ways.
1. Press and hold the fault reset button for 3-5 seconds
2. Press and hold the fault reset and security key simultaneously for 3-5 seconds
3. Press an dhold the fault and alarm silence buttons simultaneously for 3-5 seconds
4. Cycle the logic Power. This means to remove power from the main processor.
5. Call MGE. They have the software to reset the battery replacement alarm
Posted on Oct 21, 2011
SOURCE: I have mge galaxy 3000
sounds like you have a battery in thermal runaway. That means your battery could catch fire. I don't know what refroidissemt is. Your spelling is wrong. Go back to the UPS and write down the right alarms. Then I can help you.
Posted on Oct 27, 2011
Tips for a great answer:
Oct 19, 2011 | MGE Galaxy 3000 UPS System
Sep 24, 2011 | MGE Galaxy 3000 UPS System
Sep 09, 2011 | MGE Galaxy 3000 UPS System
Jun 08, 2011 | MGE UPS Galaxy 3000 UPS System
u must be open the tope of cape and u will see top of the back site in ups condenser I mean cooling system like AC condenser u will have to pull it off the sensor switch it sure u problem will be resolve
Sep 15, 2010 | Refrigerators
Sep 04, 2010 | MGE UPS Galaxy 3000 UPS System
Jul 29, 2008 | MGE Galaxy 3000 UPS System
21 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: