Question about LG Heating & Cooling
I need price and availability for the coil thermistor for LG unit Model # LP153H03A / Serial #008KAFX00891
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You could have a low air flow condition if the coil is freezing. Check the condition of the filter and the coil itself. If either one of these is dirty or blocked the coil may freeze.
Posted on Jun 21, 2008
Buy from one of the following sellers:
Appliance Parts from RepairClinic.com - air conditioner parts
Air Conditioning Parts,Furnace Parts, Heating Parts
Air Conditioner Parts | Air Conditioning Parts | Replacement HVAC
heatcoolparts.com, Heating And Air Conditioning Parts
Air Conditioner Parts
Air Conditioner Parts | ApplianceHelp.com
Posted on Jan 22, 2009
Tips for a great answer:
E5 indicates excessive temp. of the outside coil if on cooling, OR excessive temp of the inside coil in
heat mode. On cooling, the E5 will appear if the outside coil temp exceeds 68C. This is an indication
of condenser airflow reduced or non-existent. Using the procedure described above it is possible to
watch the condenser coil temp using the Temp down button and Medium fan speed combination to
display this temp. NB: if fans etc seem to be OK then measure thermistor resistance and refer to table
12. In case the problem is thermistor calibration.
Action: If unit is in cooling mode, examine both condenser fans are running. If
one is running then suspect a faulty motor. If both fans not running then
on units up to serial No. IBSA 01175, investigate the fan speed control
card located in enclosure on the LHS See fig 6.
If this checks OK then investigate main control card.
Fig 1, 2 or 3. Units with serial No's IBSA01176 and
onward are multi speed tapped wound motors not requiring a speed
control card. If both motors inoperative then suspect main control card
Aug 15, 2016 | Heating & Cooling
Aug 11, 2015 | LG Heating & Cooling
Oct 13, 2010 | LG Heating & Cooling
Apr 11, 2010 | Toshiba e-Studio 232 Black and White...
Apr 01, 2010 | LG LP120HED Wall/Window Air Conditioner
Mar 18, 2010 | LG Heating & Cooling
Oct 17, 2009 | LG DLE2512W Electric Dryer
Aug 01, 2009 | LG LMU360CE/LMN120CE Air Conditioner
Jul 18, 2008 | LG Dryers
Mar 18, 2008 | Heating & Cooling
24 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: