Question about Danby Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Electronic filters use static dicharges to filter the air. Unfortunately the make that clicking noise when they discharge. LG calls it a plasma filter. Clean both the regular and the plasma filter to see if that helps.
Posted on Dec 30, 2008
Buzzing noise - contactor. maybe a bug got in the contacts or maybe the coil is bad but in any case if you replace the contactor the buzz will go away.
Posted on May 23, 2009
Hello; Those roof tops can be noisy. Are you able to determine what is causing it? The fan? The A/C pump? Over tume, the vibration isolators that are rubber cushions the pump is mounted on, get weathered and hard and they no longer absorb the vibrations of the running pump. Those are easily chked and changed. The next point of excessive noise is the unit as a whole is tranmitting the combination of all the vibrating parts including its own housing. Here too we have a remedy. The roof unit has a seal between it and the camper roof around the hole it is fitted in. The seal is foam rubber and reasonably thick enougth to serve a purpose more than to seal out water and air. After and over time this seal ends up crushed from the weight of the a/c unit. Then the A/c unit comes in contact and is actually resting on yhe roof with what is now a very flat hard gaske. The roof unit is now vibrating the roof. This is as destructive as it is annoying. Ok? Now let's get rid of 80-90% of the noise. Check and replace compressor vibration isolator mounts. There are 4 bolts holding down the A/C unit. Sccess them from the inside by removing the ceiling trim and cover.There should be one on each corner. Bolts removed, one person push up on the unit and another on top lifting the unit. There are wires going to the unit and those may need to be disconnected. Clean the roof and the a/c where yhe seal goes.You can get a new seal from camping world or rv supply. Have your measurements, Unit make and model when you go.Assembly is just backtracking. On assembly, thinhs to pay attention to are:
Put the new seal on the A/C unit, not on the roof. It takes two people to ligft and set the unit back into the hole and center it in the hole. Don't slide it on the seal. lift it if it hs to be moved or the seal may roll over..
The wiring disconnected earlier must be dealt with and put in place for reconnecting.
Now start the bolts that hold the unit down.
Make sure-- Unit is centered
Wires can be reconnected
The four hold down bolts have their washers.
Someone go topside and verify the seal is properly in place. Measureing the for corners fo even height is one way to ck and looking under the unit is another. Now tighten the four bolts evenly. corner to cross corner. measuring again will help confirn its pulled down evenly. Pull it down no more than 1/4 to 5/16 of the seal thickness. Wire it up and put the trim and plastics back on and light it off. (run it and ck for noise and vibration. NOTE!!! The A/C unit cannot touch any solid part of the roof. Reason it was centered. Always ck the unit before each trip as you would any other psrts on the exterior of the camper. Good Luck Angie.
Posted on Sep 16, 2009
no,check to make sure the pump is secured to frame,then stay by unit have someone turn the unit on and watch the pump.sounds like the pump is loose or a spring in side the pump has broken in which case would have to replace pump.
Posted on May 18, 2010
Tips for a great answer:
Sep 14, 2011 | Carrier 38CKC036 Air Conditioner
Jun 19, 2010 | Sharp Comfort Touch AF-R120EX Air...
Jun 14, 2010 | Dodge Grand Caravan Cars & Trucks
Apr 26, 2010 | Goodman CPLE24-1 Air Conditioner
Aug 09, 2009 | Fedders Q Chassis AEQ08F2E Air Conditioner
Jun 16, 2009 | Danby Portable Air Conditioner
May 27, 2009 | Ruud Handle Air Conditioner
May 05, 2009 | Amcor A12000E Nanomax Portable Air...
Dec 06, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
Aug 16, 2007 | LG Electronic Window Air Conditioner
14 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: