Question about Generac GUARDIAN Liquid-Cooled Standby Generator -25 kW - QT02516ANSN
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Generac Guardian 15kW Generator
That sounds just about right, if the relay contacts get welded together it sometimes takes out the driver on the printed circuit board. As you found out, 12vdc from 23 to 194 makes the transfer switch move to the Generator position, relay not energized makes the ATS move to the Normal position.
You can make a nice test function by installing a 10 amp contact switch in series with either the N1 or N2 terminals. When the switch is open the generator thinks the Normal power has failed.
Posted on Jan 26, 2009
I install and work on these everyday. If you hooked up the transfer switch you probable have a control wire wrong. check the utility power sense wire. That lets it no when to start in auto. it could be a relay or fuses. or a control board.
Posted on Jul 09, 2009
Tips for a great answer:
Feb 08, 2016 | Generac Guardian Air-Cooled Standby...
Dec 12, 2015 | Generac GUARDIAN Standby Generator 10 kW/9...
Nov 11, 2014 | Generac Guardian Electrical Supplies
May 23, 2014 | Generac 5793R iX2000 iX Series 2000 Watt...
Jul 20, 2011 | Generac Electrical Supplies
Apr 23, 2011 | Generac Power Systems Generac 5928 Nexus...
Jan 03, 2010 | Generac Guardian Quietsource 25,000 Watt...
Feb 23, 2009 | Generac Electrical Supplies
47 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: