Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
E-6-Indoor unit heat exchanger sensor [ThIR] defective (resistance is open circuit or closed circuit).
• Poor connection of sensor connector on the indoor PCB.Rectify or replace sensor.
Posted on Jan 05, 2011
Tips for a great answer:
Apr 03, 2016 | Heating & Cooling
Jan 23, 2016 | Heating & Cooling
Jan 01, 2016 | DeLonghi Heating & Cooling
Nov 17, 2015 | Midea Westpointe, 12,000 BTU, Thru The...
Jun 26, 2012 | Heating & Cooling
Aug 01, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Apr 05, 2010 | DeLonghi CF210 Portable Air Conditioner
319 people viewed this question
Usually answered in minutes!