Question about Sanyo Split System Air Conditioner
Leaking water out the front of the unit
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Here is links for all the manuals for your unit.
The following are located at the above link:
Posted on Aug 22, 2009
Air conditioners wring moisture from the surrounding air that collects in a pan under the cooling coil in the inside unit.
Chances are that the condensate drain is plugged or the drain pan is plugged. Look for a hose that exits the inside unit and runs to a drain. You can follow it back to the drain pan of the A/C unit. If there is water sitting in the pan, then either the hose or pan or both are plugged.
Turn the unit off, get a small bucket and remove the drain tube. Catch the water in the bucket. Blow through the drain line until it's clear. If the thought of doing this is too repulsive, then use an air compressor or even a manual tire pump. Now check the drain pan in the unit for debris and remove as much as possible from the pan and the drain fitting.
Both the pan and drain line should be checked at the beginning of each cooling season.
Reinstall the drain tube and see how it works!
Posted on Jan 08, 2010
The leakage is probably from condensation and there should be some sort of drain for it. You should check to see if it is clogged or partially clogged. Also since you say it does it when it hasn't operated for a while you may want to check out where the lines pass through the wall and make sure that it is sealed up there so you don't get leakage from out side.
Posted on May 04, 2010
The condensate drain line was not properly installed. Make them pull the wall unit and correct the problem.
Be persistant until you are satisfied they have the problem corrected. Do not pay any additional money. If they do not correct the problem then report them online to the state board of heating and air. Fill out their requested complaint form and follow thru with a second complaint if you do not get total satisfaction from the contractor that installed the unit.
Hope this helps.
Posted on Sep 23, 2011
Tips for a great answer:
Jul 27, 2014 | Sanyo Heating & Cooling
Sep 23, 2011 | Sanyo Split System Air Conditioner
Jul 04, 2011 | Sanyo Split System Air Conditioner
Jun 29, 2011 | Sanyo Split System Air Conditioner
Dec 18, 2010 | Sanyo Split System Air Conditioner
Aug 21, 2010 | Sanyo Heating & Cooling
Aug 10, 2010 | Sanyo Split System Air Conditioner
May 04, 2010 | Sanyo Split System Air Conditioner
Aug 18, 2009 | Sanyo 12KHS71 Split System Air Conditioner
May 23, 2009 | Sanyo Split System Air Conditioner
97 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: