Question about Hayward 100,000 Btu Heater For Ag Pool And Spa H100id1
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Also if the filter is heavy with dirt, try recycling the filtering element, (sand od Diatomea sand) add new for a fresh start, this use to solve my problem.
Posted on Apr 25, 2009
There are many different things it could be with the fan comming on that means the heater is trying to fire. Make sure gas supply is on first of all. Depending on the gas line run you may have to try several times of turning on and off the heater to reprome the line. If no luck with that the next step is the igniter follow the small tube comming off the gas valve and folliw it to the burner tray try poking a small peice of wire through it from a wire brush it probally is plugged. Heater should fire after that.
Posted on Jun 26, 2009
SOURCE: Heater won't stay lit
On your main gas manifold you have orfaces that screw into it at each burner. Remove these and see if their are small spider webs in them. They will look like little lint balls. They can keep your main burner from getting gas and in turn keep the heater from sensing flame. The pilot lights and the heater starts but no flame at the main will shut it rite down. See if this helps.
Posted on Dec 18, 2009
Tips for a great answer:
Apr 22, 2017 | Hayward Pool & Spa
Jun 07, 2015 | Hayward Pool & Spa
May 16, 2013 | Pool & Spa
Feb 04, 2013 | Pentair Minimax NT Heater
Aug 31, 2011 | Hayward 100k Btu Propane Gas Pool Heater...
Jan 21, 2011 | Blue Flame Charmglow 30K BTU NG Vent Free ...
Sep 29, 2010 | Hayward 250kbtu Ng Pool Heater - Inground
Sep 06, 2009 | Pool & Spa
Jul 30, 2009 | Hayward H Series
May 07, 2009 | Hayward H400FDN Low NOx Natural Gas Pool...
118 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: