Question about Cooper Wiring Devices 277W-BOX SINGLE POLE SWITCH & RED NEON PILOT LIGHT
I have a light in the garage that has the switch inside the house. The switch worked for several years and when the light was on in the garage the pilot light was on at the switch. Something happened and now the light never goes on in the garage ( I have changed the bulb and made sure it was a good one) and the pilot light on the switch never goes off. Any suggestions?
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Depends on whether you want the pilot to glow when the circuit is live (the main light is on) or to glow when the circuit is off. (The switch can be used either way, and I have used this switch in both configurations at different places.)
The wiring diagram is on the inside of the box.
In indicates that if you want the pilot light to glow when the circuit is off, then you only need two wires (the live and the return, usually colored black and white, respectively). However, you also need a ground. The instructions say that you need the ground for safety (and probably legal code) reasons, but I suspect that, without the ground, the pilot light won't work in this configuration.
However, if you want the pilot light to glow when the circuit is on, you probably need a three wire configuration (plus the ground).
Hope this helps.
Posted on May 05, 2009
If I understand correctly you have a circuit with 4 light switches.
None of the 4 switches work, yet all 4 test for 115Vac.
Test each screw on switch to bare ground to get reading.
This problem could be loose neutral wire inside the switch boxes or anywhere along the line, or inside breaker box. Check white wires.
All 4 switches connect back to breaker box on white neutral wire that connects to neutral busbar inside breaker box.
Add a comment for more free help.
Also take advantage of fixya phone service.
For a price, expert speaks with you over phone while you work on circuit or any do-it-yourself project.
Fixya is always less expensive than a service call.
Posted on Feb 10, 2011
Tips for a great answer:
Mar 02, 2015 | Heating & Cooling
Oct 29, 2012 | General Electric GE 24-Hour Power Strip...
Aug 24, 2012 | Leviton R01-PR180-1LI Decora 180 Degree...
Dec 31, 2009 | Vanguard International VN18B Infra-Red...
Sep 08, 2009 | Mr. Heater Suspended Garage Heater
Jul 18, 2009 | Jandy Lite 2 Natural Gas Pilot Light...
Apr 20, 2009 | RTO Atwood Water Heater - 6 Gal LP
Jan 07, 2013 | Cooper Wiring Devices 277W-BOX SINGLE POLE...
147 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: