Question about Heating & Cooling
Troubleshooting york hvac ac after 30 mintes E4 error code
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: WRAC has E4 on display
E4 means return air sensor error, if the error cannot reset may be the return air sensor is out of range or defective. But if the sensor is ok you need to replace the control board itself. The reading of return air sensor is 8k to 10k ohms @ 25deg. C temperature.
Posted on Jan 13, 2008
16. SYSTEM RESET
a. Turn the ON/OFF switch to OFF position.
b. Simultaneously depress and hold the MODE and ZONE
push-buttons while turning the ON/OFF switch to ON.
FF should appear in the LCD display until the MODE
and ZONE push-buttons are released.
c. When a dip switch is turned on or off after initial configu
ration, a system reset will need to be done before the
Comfort Control CenterTM will recognize the updated selection. Try this. This is for the five button thermostat. Did you check the dip switches to be sure the proper ones are turned on? I need to know which stat you have 4 or 5 button. I have trouble shooting for both.
If you notice reset needs to take place after a dip switch is turned on or off. The dip switches are on the circuit board. You need to drop the lower cover. the dip switches will read in this order #1 heat strip/ #2 zone2/#3zone3/ #4 zone4/#5 furnace/#6 differential/#7stag/#8 gen start. Check this out and be careful. Turn off the stat to change dip switches. On will be toward the description. If you don't have remote start gen set the dip should not be on. If you dont have a Zone 3 the dip should not be on, etc.
Any questions feel free to post back
Thank you for using fixya
Posted on Mar 26, 2009
Tips for a great answer:
May 30, 2016 | Heating & Cooling
Dec 05, 2015 | Heating & Cooling
Nov 16, 2014 | Heating & Cooling
Jan 15, 2011 | Soleus MA-9000AH Air Conditioner
Dec 14, 2010 | DeLonghi PAC85 Portable Air Conditioner
Jul 12, 2009 | GE APH10AA Air Conditioner
Oct 22, 2017 | Heating & Cooling
19 people viewed this question
Usually answered in minutes!