Question about Heating & Cooling
Posted by Anonymous on
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
I'm not sure exactly what unit you have and what controls you have installed on the unit. But....there usually is a flash code schematic on the unit. Usually on the inside of the blower compartment cover. This should tell you what is wrong with the unit. It could have a low voltage short somewhere and is loosing the call for cool. So the answer can be a possible yes to your question but without knowing the flash code, it's hard to tell from my point of view. You might end up calling a service professional out to check it.
Posted on Mar 30, 2009
My unit is giving me the same alarm. If you have found the solution, please email me at firstname.lastname@example.org
Thank you very much.
Posted on May 10, 2009
SOURCE: ice formation in the indoor unit
you need to have the unit checked for the amount of freon in the system this must be done with a gauge set the freon amount is obviously incorrect
also the a-frame evaporator must be sealed in the furnace cabinet
Posted on May 28, 2009
SOURCE: we have a msz-ga80va split
Just had the same thing happen to us with the same model (right on Xmas day).
Checked the circuit breaker is on in the fuse box. Power is on to the external unit. Filters are clean.
Internal unit activates... both indicator lights on. After 5 minutes blowing air it stops and the right indicator light goes out and the left indicator light blinks constantly.
The troubleshooting guide inside the internal unit (under the outer cover you open to clean the filters) suggests that 14 blinks is an abnormality with the external unit and refer to service manual.
Think we'll be calling a technician.
Posted on Jan 02, 2011
Tips for a great answer:
Sep 30, 2017 | Hitachi Heating & Cooling
Dec 28, 2014 | Samsung Heating & Cooling
Jun 18, 2012 | Hitachi Heating & Cooling
May 03, 2017 | Heating & Cooling
4 Compressor discharge protect
5 Low pressure/Overcurrent protect
6 Indoor-outdoor communication error
8 Hi-Temp protect
10 AC Voltage Low
Each of these has maintenance required steps to resolve the errror. Let me know how many blinks your getting...
Apr 25, 2011 | LG Heating & Cooling
Apr 07, 2011 | Heating & Cooling
Feb 18, 2011 | Mitsubishi MSZ-A15NA Split System Air...
Feb 04, 2011 | LG LS-L1210CL Mini Split Air Conditioner
Jan 27, 2011 | Heating & Cooling
24 people viewed this question
Usually answered in minutes!