Question about Heating & Cooling
Posted by Anonymous on
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Split System Air conditioner
There normally two types of leakages from the wall unit.
1.The warm air in the room when comes in contact with the cooling coil of heat exchanger (consisting of fine fins where compressed refrigerant evaporates) looses its heat & cannot retain the same moisture content at lower temperature at the point of contact with evaporator. There is a provision of a drain pipe to carry this condensed water to outside water drain. So if the drain pipe is choked or the coupling joint of the drain pipe at the bottom of cooling coil is not proper, there will be water leakage, This can be easily attended by physically looking at the fittings.
2.The second problem can be the leakage of the refrigerant. If there is second type of problem, then there will be very little or no cooling irrespective of continuous running of air conditioner. This can be easily checked by feeling the temperature of outlet air from the air conditioner.
Conclusion-As you have written that there is leakage from the air conditioner, but you have not written whether it is visible or invisible. If the leakage is visible, it is problem number 1 & if it is invisible, it is problem number 2.
If you are not satisfied you are free to ask for more explanations.
Posted on Jan 29, 2008
Do you mean thermostat, the wireless controller for air conditioner? we are exporter of this line from China. Should you be interested in our products. Please feel free contact me at email@example.com or add my MSN firstname.lastname@example.org. Our website is www.yseagroup.com
Posted on Oct 20, 2008
The simplest way of explaining this is as per the following. On your outdoor compressor unit there should be two pipes, one smaller diameter [high pressure] and a larger diameter pipe [low pressure]. Turn your A/C on inside the house and then shut off the smaller diameter pipe. Run the unit for a around 3 to 4 minutes and then check if the cooling is reducing from the unit inside the house. When you feel room temperature air [not cool] being emitted from the indoor unit shut off the larger diameter pipe and turn off unit. Isolate electrics, disconnect A/C piping and immediately seal the piping with good quality tape to prevent egress of dirt. When re-installing a quick purge of gas is usually only required to clear the lines if they were sealed properly and kept clean. Ideally running a vacuum pump is recommended but if care was taken then it may not be needed, as in many of my installations.
Posted on Nov 13, 2009
5 flashing is ' compressor drive' and check the high pressure, condenser fan motor capacitor for proper running
Posted on May 21, 2010
Tips for a great answer:
Oct 08, 2015 | LG 18000 BTU Dual Zone Mini-Split Heat...
Sep 28, 2015 | Samsung AQV36JA Classic 36000 BTU Single...
Jul 16, 2015 | Fujitsu 15,000 Btu/h 21 Seer Single Zone...
Jan 07, 2015 | Mitsubishi MS-A09WA Split System Air...
Jul 04, 2011 | Sanyo Split System Air Conditioner
Oct 30, 2017 | LG LSC091PMA Split System Air Conditioner
May 16, 2010 | LG LM-2430C2L Cool Mini Split Air...
Apr 08, 2010 | Sanyo Split System Air Conditioner
Jul 20, 2009 | Toyotomi TIN/TIG-329D Air Conditioner
32 people viewed this question
Usually answered in minutes!