Question about Heating & Cooling
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
It's 'possible' but not likely that you need additional freon.
What is more likely is the 'filter' (for inside coil) is dirty and possibly the coil itself - and/or - the outside coil is dirty.
I would check out the filter - if dirty - I would change it and would also inspect the inside coil. If it's also dirty I would clean it the best I could (with a brush of some sort).
I would also check the outside coil and clean it if need be.
Hope this helps.
Posted on Jun 11, 2010
SOURCE: E3 ERROR COMING IN HUKE
E3 Outdoor activation of high pressure switch. Due to over charged gas/condenser block/less rpm fan motor.
If overcharged release the over charged gas./clean condenser/replace fan capacitor.
Posted on Dec 19, 2010
Tips for a great answer:
Sep 27, 2017 | Heating & Cooling
Jul 25, 2016 | Celiera Celi 24000 BTU Ductless Mini Split...
Mar 22, 2016 | Sanyo 12000 Btu Mini Split Air Conditioner...
May 13, 2014 | Haier HEATER CPN10XH9 Air Conditioner
Jun 16, 2011 | Heating & Cooling
May 01, 2011 | Heating & Cooling
Jun 09, 2010 | Fujitsu 24R1 Air Conditioner
Mar 30, 2010 | Heating & Cooling
Jul 03, 2009 | Toyotomi TIN/TIG-329D Air Conditioner
30 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: