Question about Heating & Cooling
HELP! I cant turn off my mini split, the remote control is on but apparently it needs to be reprogrammed
Posted by Anonymous on
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check each screw on your compressor to ground (compressor case). Should be very high resistance Then check the resistance across your teminals on the compressor to be sure it is not shorted. Then check the wiring to your capacitor (The big one). I ran across this just last week. The mechanic didnt have the capicator wired correctly. If it is brand new it will have a wiring schematic somewhere on it.
Dont leave the compressor on very long, but turn it on long enough to get a voltage reading across the terminals. I assume it should be 240 volts. If you have check all of this, they make a jump start gadget to start a stuck compressor. They sell it just about everywhere. Let me know how this comes out..
Posted on Sep 30, 2008
SOURCE: Carrier air handler tonnage?
That is a fairly large difference. It is usually ok to have the inside evap. coil and blower up to 1 ton larger than the outside condenser. That will make the unit slightly more efficient as well as less likely to freeze up on low airflow situations. It is not recommended to install a new condenser on an old evap coil. There has been a lot of changes to the design of the coils in the last little while. For example a 10 year old 2 ton coil may only have 3 cubic feet of volume but a new 2 ton coil may have 4 cubit feet of volume.
There are many factors that may have infulenced the decision on what size condenser to install. Many of which can only be done by visiting the home and doing alot of work, checking the duct sizing bioth supply and return, inspecting the insulation and windows of the home etc. etc. Most of the time that never gets done. You can blame the contractor for not doing a complete check, but at the same time you can blame the customer because many contractors that are that good loose the job to a cheaper bid that did not no any of the research. It is a catch 22 for everyone involved.
There is ALOT more to sizing equipment that many people think, sadly that also includes many HVAC contractors. Way too many people use "rule of thumbs" or flat out "guess".
Sorry for the rant but your queston can only be answered by a good well educated HVAC contractor visiting your home. That type of a contractor is getting hard to find these days in such a price competetive world.
Posted on Oct 14, 2008
Don't know a code for a universal remote, but you can order a new remote from an appliance parts supplier. If you have the model you posted under, the part number would be WJ26X10152 . (about $25) Make sure you have your exact model number from the model / serial number tag off the product to make sure you get the correct remote.
Posted on Jul 29, 2009
CA: Compressor Discharge Sensor Fault
Contact a qualified service technician and have them replace this sensor.
Posted on May 04, 2010
i want know that how can connection wiring of indoor panel and out door panel 0f carrier 42qg24-c / 38qg24-c ?
(i need wiring diagram)
Posted on Jul 06, 2010
Tips for a great answer:
Oct 20, 2016 | Carrier Heating & Cooling
Jul 25, 2016 | LG LS-K1830CL Cool Mini Split Air...
Nov 25, 2015 | Heating & Cooling
Jan 21, 2015 | Carrier Heating & Cooling
Jan 12, 2015 | Carrier Heating & Cooling
May 14, 2014 | Samsung AQV18JA Classic Wall Mounted Mini...
Sep 18, 2011 | Heating & Cooling
May 14, 2010 | Haier HSU22VCA 22000 BTU Cooling Only Mini...
29 people viewed this question
Usually answered in minutes!