Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Generally when an ac trips the main breaker and the breaker its self isn't bad, the compressor is going bad or is bad. To check you will need to do an ohms test on the compressor. If you get a reading of less than infinite, then the compressor is bad. You will need to test every lead going to the compressor which is usually 3 unless you have a crank house heater installed but they are not typical on a small unit. If the compressor has gone bad it is possible the it took the board out as well.
Posted on Mar 31, 2009
i had this problem it was freezing up outside it was only a short pipe run so it was over gassed i took some out and it was fine
Posted on Jan 18, 2010
Posted on Jul 05, 2013
Tips for a great answer:
Feb 15, 2016 | Heating & Cooling
Jan 18, 2016 | Gree Rio High Efficiency Ductless Mini...
May 24, 2014 | Gree 24,000 BTU 18 Seer Ductless Mini...
Sep 07, 2013 | Gree 18000 Btu 20 Seer Ductless Mini Split...
Aug 05, 2012 | Heating & Cooling
Feb 09, 2010 | Heating & Cooling
Dec 24, 2009 | LG LS-L1210CL Mini Split Air Conditioner
22 people viewed this question
Usually answered in minutes!